## What should my Pressures be for R-410A?

For R-410A, a working pressure capability of at least 400 psi is recommended (this includes recovery cylinders). Standard DOT recovery cylinders rated for 350 psi should not be used.

What should 410A pressure be at 85 degrees?

The vapor pressure is 118 PSIG and because it is 85°F outside, the R-410A bottle pressure is 254 PSIG. The pressure in the bottle is much higher than the pressure on the low side of the system so if they are connected, refrigerant will exit the bottle and enter the system.

### What is the pressure of R-410A at 72 degrees Fahrenheit?

208,4 psig
Example: What is the pressure of r410a at 72 degrees Fahrenheit? We can see that at 72°F, the R410A pressure is 208,4 psig.

What happens if you put R22 in a 410A system?

Understand this: The mineral oil in a compressor has a vapor pressure. If that’s so, then what R22 there is in the system can never evaporate under the higher suction pressure of R410a. It will just flood back to reduce the compressor life and will greatly reduce the system capacity.

#### What should suction line temp be 410A?

The suction temperature should be above 35°F and below 65°F entering the compressor and the discharge line temperature should be below 220°F and above 150°F (typically) on a properly functioning package unit.

What happens if you overcharge 410A?

If the system is overcharged, part of the refrigerant cannot be evaporated, and the compressor will work with the refrigerant in liquid phase. Consider the refrigerant R-410A: the pressure in the evaporator is 93.2 psia, according to the Table 8 (ASHRAE, 2013).

## What is a good subcooling for 410A?

Most heating and cooling systems should operate at a superheat of 10F at the evaporator and between 20F to 25F at the compressor. if your HVAC system has a thermostatic expansion valve (TXV), the subcooling should be between 10F and 18F.

Can I replace R-22 with R-410A?

The answer: No. Putting R-410A refrigerant into an AC unit that was designed to use R-22 will cause the unit to die soon after it tries to run.

### Can R-22 and R-410A be mixed?

R-22 and R-410a are both refrigerants, true. They can both be used in air conditioners or heat pumps to cool your home during summer. You should never, ever try to mix them in the same system, or use them in a system not rated specifically for that kind of refrigerant.

What do you need to know about R410A?

R-410A is a Hydrofluorocarbon , ( HFC), made up of hydrogen, fluorine , and carbon atoms. It lacks the chlorine, believed to be harmful to the environment. R-410A has zero ozone depletion potential.

#### Which type of gas are R32 and R410A?

For example, both R32 and R410A belong to a group of gases called hydrofluorocarbons. Their ODP (ozone depletion potential) is 0, which makes them eco-friendly. Both refrigerants belong to the same group and share the same ODP. However, in this article, we will discuss their differences.

What are the correct pressures for R410a?

An R-410A system may be operating at over 600 psi and not have the high-pressure safety switch open. Carrier has a unit with the high-pressure switch set at 610 psi. It resets at about 420 psi. The same model has a loss-of-charge liquid-line switch that opens at about 20 psi and resets at about 45 psi.

## Which is colder R22 or R410a,?

The difference between R22 and R410a is not one of which is colder. The difference is that they are used in systems that use different operating pressures. You can not add just any ‘ol refrigerant to a given system.